The Properties of Grounding Distance using the Kingsine Relay Test Set
|Kingsine K10\K20\K30 Series
Device: GE L90 Line Differential Relay
Fixed Value Menu:
Grounding Distance Graph (GE Software)
A. Connect the output terminals of three-phase voltage and current IA of the relay test set with the corresponding input terminals of the protection device by test wire.
B. The triggering contact of the protection device is connected with Binary Input terminal A of the relay test set.
C.Open Advanced Distance I module,setting test parameter
Time and Fault Type
After the setup is finished, click ‘Run’ button on the right upper corner and begin the test
Latest posts by Mike Novello (see all)
- CONSULTIX WTX-35-A4 CW Test Kit For Sale - November 9, 2021
- Biologic SP-150 Single Channel Potentiostat and VMP3B-80 Booster For Sale - September 7, 2021
- ROTALIGN Ultra iS Intelligent Alignment System For Sale - May 12, 2021